Remote Communications & Overview Displays
Simple Network Management Protocol (SNMP) Gateway
The DSE892 connects DSE control modules to external SNMP systems. Once a connection is made full monitoring and control functionality becomes active. The gateway device specialises in monitoring the instrumentation and operating state of the connected DSE control module.
85 mm x 149 mm x 51 mm (3.3” x 5.8” x 2.0”)
0892-01 - 892 Simple Management Network Protocol (SMNP) Gateway
Request a Quote
CONTINUOUS VOLTAGE RATING
8 V to 35 V Continuous
Able to survive 0 V for 50 mS, providing supply was at least 10 V before dropout and supply recovers to 8 V. This is achieved without the need for internal batteries. LEDs and backlight will not be maintained during cranking.
MAXIMUM OPERATING CURRENT
200 mA at 12 V
110 mA at 24 V
MAXIMUM STANDBY CURRENT
150 mA at 12 V
90 mA at 24 V
COMMUNICATIONSUSB (Single DSE Controller)
RS232 (Single DSE Controller)
RS485 (Multiple DSE Controllers)
Ethernet (Multiple DSE Controllers)
Ethernet SNMP & SMTP
Environmental Testing Standards
BS EN 61000-6-2
EMC Generic Immunity Standard for the Industrial Environment.
BS EN 61000-6-4
EMC Generic Emission Standard for the Industrial Environment.
BS EN 60950
Safety of Information Technology Equipment, including Electrical Business Equipment.
BS EN 60068-2-1
Ab/Ae Cold Test -30°C.
BS EN 60068-2-2
Bb/Be Dry Heat +70°C.
BS EN 60068-2-6
Ten sweeps in each of three major axes.
5 Hz to 8 Hz @ +/-7.5 mm, 8 Hz to 500 Hz @ 2 gn.
BS EN 60068-2-30
Db Damp Heat Cyclic 20/55° C @ 95% RH 48 Hours.
BS EN 60068-2-78
Cab Damp Heat Static 40° C @ 93% RH 48 Hours.
BS EN 60068-2-27
Three shocks in each of three major axes 15 gn in 11 ms.
0892-01 - DSE892 SNMP GATEWAY